|Model Name:||YJV||Conductor Type:||Class 2 Annealed Copper|
|Size:||1.5~630mm²||Nos.of Core:||2~5 Cores|
|Sheath:||PVC||Applications:||Distribution Networks, Industrial Installations|
|Temperature Rating:||-25℃~90℃||Warranty:||12 Months|
630mm2 Low Voltage Power Cable,
3,4,5 Copper core electric power cable YJV YJV22 0.6/1kv
1kV for Fixed installations such as distribution networks or industrial installations.
a, Number of cores:1, 2, 3, 3+1, 3+2, 3+3, 4, 4+1, 4+2, 5 and so on.
Conductor: Solid or stranded copper
Insulation: Cross-linked polyethylene (XLPE) or Polyvinyl chloride (PVC)
Filler: Polypropylene filament with lapped binding tape
Binder: Binding tape
Inner sheath: Polyvinyl chloride (PVC)
Amour: Galvanized steel wire armored(SWA) or steel tape armored(STA)
Sheath: Polyvinyl chloride (PVC)
c, Nominal Section
Area(mm2) :1.5 2.5 4 6 10 16 25 35 50 70 95 120 150 185 240 300 400 500 630 800d, Features
XLPE insulated power cable do not has excellent electric, mechanical properties,but also has powerful resistance against chemical corrosion,heat resistance and enviromental stress resistance. Its structure is simple. The long period operating temperature is +90 °C. It is conveninet to use and can be laid with no restriction of different level.
XLPE insulated steel wire armoured power cable: XLPE/PVC insulated power cable has a number of advantages over paper insulated and PVC insulated cable. XLPE cable has high electric strength, mechanical strength, high-ageing resisting, environmetal stress resisting antichemical corrossion, and it is simple construction, using convenient and higher operating of long term temperature. It can be laid with no drop restriction.
Various of flame-retardant and non-flame retardant XLPE cable can be manufactured with three technology(peroxide, silane and irradiation crosslinking). The flame-retardant cable covers all kinds of low-smoke low-halogen low-smoke halogen free, and non-smoke nonhalogented and three classes ofA, B, C.
1) These cables are most suitable for direct burial or for installation on trays or ducts, Where there is a risk of mechanical damage, armoured cables should be used.
2) For laying in ground along route with large difference of level able to bear external mechanical forces.