|Model Name:||KVVRP||Rated Voltage:||450/750 V|
|Conductor Type:||Stranded Annealed Copper Class 2||Sheath:||Pvc|
|Armour Type:||Steel Tapes|
20mm2 shielded Electrical Control Cable,
20mm2 Electrical Control Cable,
20mm2 XLPE shielded electrical wire
▼ Delivery Port :
|Port of Shenzhen||Port of Hongkong||Port of Guangzhou|
* How to assure the quality of products?
1. Most of our products have certification.
2. Our Lab staff will test the material and check the process card before production.
3. The O.D tester is testing all the time during production, and the production line is always under control.
4. The product will be tested by Lab staff after production.
* Do you offer free samples or not?
1. If we have inventory about the sample you need and the total amount is not large, it's free.
2. If we don't have inventory, according to our company's rule, sample and freight costs need to be paid by your esteemed company. And we will return the sample cost to you when you place the first order with us. Thanks for your support.
* When I want customized products, how to do it?
We have professional equipment, technicians & skilled employees, OEM & customized service is welcome. Drawings or samples are required. Of course, the purchased quantity should meet our MOQ.
Fire-resistant,Flame-retardant,Low-halogen,Non-halogen,Low-fume,Low-smoke ( LSZH ) ,as well as acid-alkali-proof,High temperature resistant,Termite and Rodent resistant, Water proof series and so on.
|Conductor material||stranded annealed copper Class 2|
|Conductor flexibility||Stranded class 2 to IEC 60228|
|Insulation||Cross-linked Polyethylene XLPE according to IEC|
|Inner sheath||PVC(Polyvinyl Chloride) Type PVC/ST2 according to IEC|
|Armour type||Steel Tape|
▼ Installation Condition :
[Installation temperature ]: 5 ℃
[Minimum bending radius ]: 6 X cable diameter
[Recommended maximum tensile stress]: 50 N/mm2
▼ Technical Data:
|Rated Voltage Uo/U||450/750v|
|Test voltage :||3000 V|
|Permissible operating temperature at conductor||+70°C|
|short circuit temperature ( duration max. 5 s)||160 °C|
|Minimum installation temperature||-5 °C|
|Max. conductor permissible tensile stress||50 N/mm²|
|Minimum bending radius||6 x cable Ø|